Energy Monitoring SystemF-MPC I/O Unit series
- The energy monitoring system uses the F-MPC-Net communications protocol to monitor ON/OFF status, measure pulse signals, output alarm relays, and read flow meters.
- Use the DI/DO Unit to input ON/OFF signals, count total pulses, and control the ON/OFF status of relay outputs.
- Use RS-485 2-wire communications to send input status to a host, control relay outputs with ON/OFF commands from the host, and more.
Types and ratings
(1) DI (Digital Input)There are 6 digital inputs, and they can be used to read ON/OFF status and count pulses.
With 2 of the 6 digital inputs, pulse widths of 10 ms or longer can be counted.
With the other 4 digital inputs, pulse widths of 50 ms or longer can be counted.
ON/OFF status can also be sent via communications.
The total count values for pulses can also be sent via communications.
(2) DO (Digital Output
There are 4 digital outputs and their ON/OFF status can be controlled via communications.